Powder fire extinguisher 2kg BC/ABC - " TORNADO "Charged, fully equipped (valve, manometer, hose, wall bracket),
with CE marking, EN3
(Outside diameter): f 110 mm
(Cylinder length): 310 mm
(Weight of the cylinder): 1 kg.
(Weight of the fire extinguisher): 3.7 kg.
(Contents of the powder in the extinguisher): 2 kg.
(Temperature range): -30C + 60C
(Maximum working pressure): 18 bar
(Test Pressure): 27 bar
(Working gas): Nitrogen
(Minimum thickness of the cylinder): 1.07 mm
(Fire class): 13 A 70B C
(Package size): 12 x 13 x 41 cm
Fire extinguishers are designed for fire ignition or initial fire
of solid material which are easy flammable and combustible liquids,
gaseous substances and electrical systems under pressure up to 1000
V under the technical characteristics of products
Equipment of buildings (residential, public, commercial,
manufacturing, agricultural and mass gatherings of people, etc.),
facilities, installations, vehicles and other machinery.
GENERAL STRUCTURE AND PRINCIPLE OF OPERATION
All fire extinguishers consist of extinguishing substance, metal
cylinder for storing its vent gas valve with safety valve, pressure
gauge (for fire extinguishers with module H), with nozzle or hose
nozzle (gun) to guide the flow, label form of BDS EMZ, seals and
Fire extinguishers works on the principle of suppression of fire
extinguishing substance to the fire under the impact ejection gas.
INSTRUCTIONS FOR USE
Use of powder, water, foam and CO2 fire extinguishers of type H
broke the seal and pull out its preventive pin. Point the hose
(nozzle or gun) to the outbreak of the fire and press or rotate (as
structure) the valve.
PACKAGE AND STORAGE
Fire extinguishers are packaged in paper or polyethylene packaging
and stored in a dry ventilated space, protected from direct hit of
sunlight at temperature from +5 C to +30 C.
INSPECTION, REPAIRING AND RECHARGING
All fire extinguishers shall be inspected after each use and
periodically not less than once a year. Inspection, repairing and
recharging is carried out with spare parts and fire-fighting
substance certified by the manufacturer to repair it.
SCRAP OF THE FIRE EXTINGUISHERS
Fire extinguishers, their components and extinguishing substances
are discarded when it is impossible to be recovered.
INSTRUCTIONS FOR SAFETY OPERATIONS
Do not extinguish ELECTRICAL systems under high voltage with water
and foam fire extinguishers and installations! Electrical
installations with voltage to 1000 V extinguish with fire
extinguishers and systems with powder and CO2 with the minimum
distance of 1 meter.
It is not allowed to use the fire extinguishers if you are not
familiar with the safety instructions.